Posted 04.02.09 by Campus Safety
Safety Activity Log
On 2 April 2009 at 0453hrs Campus Safety received a call in reference to a trouble alarm at the Main Building basement. Upon arrival at 0454hrs the panel indicated a trouble alarm in the basement sprinkler valve tamper switch, alarm was silenced. No BCFD response, no problems in the Main basement.